Thermostatic faucet manual:
1. Left knob used to control the water flow, switch angle of 90 ℃, the handle on the size of the tag printed with traffic.
2. The right knob is used to control the mixed water temperature knob on the printed standard security of the mixed water temperature of 38 ℃, you must press the temperature control knob on the red button, while the counter-clockwise rotation. If you need less than 38 ℃ mixture of water, you can rotate the knob to the clockwise.
3. Check the water temperature:
When the thermostat knob counter-clockwise to security control limit (not pressing the case of security controls) water temperature should be 38 ± 2 ℃, calibrated at the factory before it is set. Calibration 38 ℃ conditions are: hot water temperature of 60-65 ℃, cold water temperature of 18-23 ℃, hot and cold water pressure is 0.35MPa. If you installed the water temperature is too high or too low, because your actual using the conditions (hot and cold water supply temperature and pressure) deviate from the factory calibration conditions, even though you adjust the temperature knob alignment 38 ℃, but the water temperature has deviated from 38 ± 2 ℃. then you can based on your actual use conditions, to re-adjust the safety standards of temperature, to meet the actual working conditions after installation. Here's how: Remove the knob cover, relieved screws, measuring water temperature with the thermometer, press the safety control button and rotate the temperature adjustment buttons, the effluent temperature of 38 ℃, remove the thermostat rotation re-assembly, so that knob 38 ℃ Positioning circle alignment mark "|" tighten the screws, covered with cover, security, temperature calibration is completed.
Please note: Hot water stopped for later, transferred to low-temperature knob position, only cold water use.